Part 8: Vertically Suspended Pumps (API Types VS1–3, VS6, VS7)
To date, we have addressed how to install DuPont™ Vespel® CR-6100 into the various horizontal pump types to eliminate metal-to-metal contact points in the pump and minimize the risk of pump seizure. This allows a reduction of clearance which improves efficiency and rotor stability.
This segment will discuss how to use Vespel® CR-6100 in vertically suspended pump types (API types VS1-VS7). These types can be further broken down as “discharge through column” (VS1, VS2, VS3, VS6, VS7) and “separate discharge” (VS4 and VS5).
In vertically suspended pumps, we can upgrade the same components as horizontal pumps (wear rings, throttle bushings, throat bushings) for the same reasons-to eliminate the metal-to-metal contact areas in the pump and reduce the clearance resulting in improved reliability and efficiency.
Today we will focus on the components which are unique to vertically suspended pumps-the vertical pump shaft bearings: line shaft bearings, bowl bearings, and bottom bearings. Vespel® CR-6100 is ideally suited to this application, particularly in services which suffer from a lack of lubricity or may run dry at startup. Vespel® CR-6100 does not seize like metal alloys, it can survive running dry, and it can withstand mechanical impacts and thermal shocks so it doesn’t break like carbon or graphite.
One thing of note is that vertical pump shaft bearings do not have differential pressure across the parts, therefore, they do not impact pump efficiency. Because the clearance of these components tends to be rather tight, to begin with, a further reduction in clearance can easily lead to assembly issues with a limited upside associated with the tighter clearance. Therefore, our recommendation for these parts is to install the Vespel® CR-6100 into the spiders or bowl assemblies with the press fit shown in our installation guide, then final machine to the original design clearance.
In our installation guide, you will find two clearance charts–one for horizontal pump types, one for vertical pump types. Because we don’t want the wear ring clearance tighter than the shaft bushing clearance, we simply recommend making the wear ring clearance 0.002″ (0.05 mm) larger than the shaft bushing clearance in these pumps. In short, we highly recommend that you download the Boulden Installation Guide for Vespel® CR-6100.
Discharge Through Column
Vertically suspended pumps are often selected because the service offers poor suction conditions such as light hydrocarbon service or condensate. In a long-term study, a refinery upgraded 22 vertical pumps to Vespel® CR-6100 wear parts. The pumps were operating in light hydrocarbons, flare knockout drum, and several stop/start services like product transfer. In the 5 years prior to upgrading the pumps, this population of pumps comprised many “bad actors” with poor reliability. In the 5 years after upgrading the pumps to Vespel® CR-6100, there were only 8 repairs on the entire population of pumps and the MTBR of this group of pumps increased to more than 10 years!
The combination of excellent reliability with ease of machining and installation along with immediate stock availability has made Vespel® CR-6100 the material of choice in these applications.
Vespel® CR-6100 can handle significant periods of dry running with minimal wear, making it easier to bring the pump online. When you upgrade your wear rings to Vespel® CR-6100 and reduce the clearance, you might also find the pump easier to start due to a reduction in the NPSHR (Net Positive Suction Head Required).
To be continued…
In the next two issues, we will address vertically suspended pumps with a separate discharge (API Type VS4) and then we will discuss installation and assembly issues unique to vertically suspended pumps.
Until then, if you have a vertical pump which is giving you headaches, consider upgrading the wear parts to Vespel® CR-6100. Contact us today. We have the Vespel® CR-6100 in stock in a wide range of sizes available for immediate delivery to nearly anywhere in the world.
For details on installing Vespel® CR-6100 into nearly any centrifugal pump type, download the Boulden Installation Guide.